OHA Drinking Water Services
Contact Report Details
|PWS ID:||OR41 94657|
|PWS Name:||WOLF CREEK GENERAL STORE|
|Who Was Contacted:||Rajesh Kumar|
|Contact Phone:||541-866-2538 (Email address hidden)|
|Contacted By:||JENSEN, NEIL (DEPT OF AGRICULTURE)|
|Assistance Type:||WATER QUALITY ALERT RESPONSE|
|Details:||I visited the retail food establishment to conduct a groundwater source evaluation request to send to the DWP. Upon visiting the store I was told by the PIC that the uv light had been fixed and that the public notice had been taken down. I instructed the PIC that the public notice cannot be removed until the problem of the E. coli source water was corrected (not simply replacing the uv light).
I asked to speak to the owner of the store and was told that Mr. Kumar was working at the Glendale store. I informed the owner that the pubic notice must be kept in place and all water used for public consumption must be boiled before using. I also informed Mr. Kumar that the water source will be reviewed by a drinking water program engineer and guidance will be forthcoming based on this review.
A source water evaluation form was completed with coordinates for the water source and Wolf Creek.
|Associated Alerts:||COLI21621 - 11/05/2021 - COLIFORM (TCR) , E. COLI See also: 11/05/2021, 11/05/2021
COLI21628 - 11/05/2021 - COLIFORM (TCR) , E. COLI See also: 11/05/2021, 02/10/2022
COLI21605 - 11/02/2021 - COLIFORM (TCR) , E. COLI See also: 11/02/2021, 11/05/2021, 11/02/2021
COLI21510 - 10/08/2021 - COLIFORM (TCR)